50-74-209. Required inspection intervals -- failure to comply with safety standards. (1) (a) All manually fired boilers and all boilers and banks of boilers rated with a total input of 400,000 Btu's an hour or greater must be inspected at least once each year.
(b) All automatically fired boilers rated with an input of less than 400,000 Btu's an hour must be inspected at least once every 2 years, except that an automatically fired boiler in a school, day-care center, hospital, rest home, retirement center, or place of assembly with a capacity for more than 100 persons must be inspected once a year.
(c) Boilers exempt under the provisions of 50-74-103 do not require inspections.
(d) Upon written application, longer inspection intervals may be authorized by the department.
(2) In addition to the inspection required by subsection (1), it is the duty of each inspector to examine at proper times, when in the inspector's opinion an examination is necessary, all boilers that have become unsafe from any cause and to notify the owner or the person using the boilers of any defect and what repairs are necessary to render them safe.
(3) If a boiler is found, upon inspection, to violate safety standards set forth in rules referred to in 50-74-101, the department shall order the owner of the boiler to comply with the standards. An owner who negligently or knowingly fails to comply with an order is guilty of a misdemeanor and upon conviction is punishable by a fine of not less than $50 or more than $100, imprisonment for not more than 60 days in a county detention center, or both.
History: (1)En. Sec. 554, Pol. C. 1895; re-en. Sec. 1643, Rev. C. 1907; amd. Sec. 5, Ch. 30, L. 1913; amd. Sec. 1, Ch. 32, L. 1919; re-en. Sec. 2714, R.C.M. 1921; re-en. Sec. 2714, R.C.M. 1935; amd. Sec. 2, Ch. 77, L. 1967; amd. Sec. 3, Ch. 225, L. 1971; amd. Sec. 26, Ch. 182, L. 1975; Sec. 69-1503, R.C.M. 1947; (2)En. Sec. 557, Pol. C. 1895; re-en. Sec. 1646, Rev. C. 1907; re-en. Sec. 2717, R.C.M. 1921; re-en. Sec. 2717, R.C.M. 1935; Sec. 69-1506, R.C.M. 1947; R.C.M. 1947, 69-1503(part), 69-1506; amd. Sec. 64, Ch. 613, L. 1989; amd. Sec. 1, Ch. 499, L. 2001.